Testing required annually (wet test) & inspections 6 monthly
Hydrants to be tested annually with dry risers
Get Your Dry Risers Inspected Today
The person responsible for a building or site is legally required to maintain all fire fighting equipment, including dry risers. The British Standard Code of Practice BS9990:2006 requires a full annual pressure test and six monthly visual check for dry risers for buildings above 18 metres and below 60 metres (buildings over 60 metres/18 storeys require wet risers), & clause 7 of the Code states that inlets, landing valves, drain valves and landing valve boxes should be inspected every 6 months and recommends that wet tests be carried out annually when the main can be checked for leaks.
Dry Riser Testing – Annual Wet Test
Dry and wet risers are checked and pressure tested to 9 bar for a minimum of 15 minutes. All insets and outlets are checked for leaks and any missing or faulty items replaced.If any valves have to be replaced a further pressure test will be carried out before certification is issued.
Dry Riser Testing – Six Monthly Visual Test
This test involves a visual inspection only as required by BS9990:2006 and any missing or damaged items are replaced.
Full certification is issued when the systems pass a thorough operational test including pressure tests to 9 BAR for 15 minutes.
For more information on any of our services, please phone us today 1890 77 22 22 or email us at email@example.com. We offer a 24/7 Emergency Call Out Service Nationwide.